Cookies are not enabled in your browser and may affect website resources. We recommend that you turn it on.
Remotely access devices connected to the AirGate-3G router, using the corporate network [internal server] of the client.
Important: When using the ROUTER in this application mode it is important to follow all the rules and requirements of the security policy of the company.
To enable the internal routing function, the AirGate-3G should be initially be configured to access the internet (via Ethernet cable). This management should be done by the manager of the company’s corporate network.
In the configuration of the 3G router we have the option of Link Management, where we are able to configure the primary interface. Select the option Eth0, as shown in Figure 1.
Figure 1 – Link Management.
Following this we should access the tab Eth0 under the menu ETHERNET, select the option WAN and configure the interface in accordance with the procedures defined by the company’s IT department.
Figure 2 – Type of Ethernet Interface
In this tutorial we will configure a static IP 192.168.1.2 as shown in Figure 2. The IT department from the company should created a rule for access within the network [overpassing the firewall and other protection allocated by IT], to provide access to the service ports of the 3G router from an external connection, through the Public IP address.
It is necessary to configure the NAT/DMZ table of management ports in order to route the connection to the desired service ports. In Figure 3, we can see the internal redirection of the service ports 18501 [download and upload software programing] and 80 [HTTP service] that are required to present the variables in a dynamic HTML page.
For more information you can find the XL family operating manuals by following the link: http://www.novus.com.br/downloads/Arquivos/man_xl6_series_english.pdf
Figure 3 - NAT configuration
Note: Cscape is the propriety software of the XL6e-HE1E4 controller that uses the service port 18501 for configuration [download and upload programing software].
Simply speaking, any connection request to connect to the IP 192.168.0.4 [the XL6e-HE1E4] will be routed through the valid Public IP to the IP 192.168.0.2 [AirGate-3G].
When connecting to the router at 192.168.0.2, it will check it´s Network Address Translation (NAT) service to verify if there are rules associated with the IP/Port.
In this application tutorial, as mentioned above, we have mapped the service ports 18501 and 80, to the IP address 192.168.0.4 [the XL6e-HE1E4].
1.2 Configuration of CLP software [CsCape]:
In the programming software it is possible to select the interface [Ethernet] to connect with the XL6e-HE1E4 controller as indicated in Figure 4.
Figure 4 – Communication interface connection.
Next, there will be a configuration screen displayed, Figure 5, where we should configure the IP Address, the mode of connection and the Port.
Figure 5 – IP Address configuration.
The communication status of the XL6e-HE1E4 controller can be seen in the bottom right corner of Cscape, as shown in Figure 6. From now on it is possible to connect remotely and download or upload your program to the device.
Figure 6- Configuration Arcitecture [Cscape].
Following this configuration, it is possible to Access remotely any device connected to the Ethernet port of the 3G router, in order to upload, download, configure, monitor in real time, acquire data or perform any other available service that is encapsulated by TCP/UDP.
Note: Public IPs are provided by Internet service providers and mobile carrier. These IPs are out of the private IP address ranges displayed in Table 1 :
Table 1- Private IPs
Range IP address
10.0.0.0 – 10.255.255.255
172.16.0.0 – 172.31.255.255
192.168.0.0 – 192.168.255.255
169.254.0.0 – 169.254.255.255
Fieldlogger was the chosen solution to measure temperature and vibration of lift pumps at the wastewater treatment plants of the company located in São Paulo. With proper monitoring, it is possible to prevent problems and save on engine maintenance.
TxIsoRail-HRT and TxIsoBlock-HRT bring the robustness of NOVUS devices combined with HART® protocol certification, recognized worldwide as an industry communication standard for smart field devices.
The pressure measurement procedure is widely widespread within industrial processes and the reliability of these measurements is related with trade, quality, health and safety issues. In this way, a wrong measurement can create problems in the quality of the industrial process and even fatal accidents. In this article, you will find some definitions and the importance of metrology within the industry.
The NP785 can operate bi-directionally, providing the ability to measure differential pressure ranges from vacuum to positive pressure. Designed for HVAC systems and industrial environment, it ensures temperature compensation for long-term stability and complies with electromagnetic compatibility standards.
DigiRail Connect can be used as a slave device in Modbus RTU networks that have RS485 interface or as a server device in Modbus TCP networks that have Ethernet.
NOVUS is committed to protect the privacy and security of your personal information. The data that you share with NOVUS allows us to provide a better experience when you use our products and services. We guarantee total privacy to your data, used exclusively for communications between NOVUS and you.
In this statement we affirm: