Cookies are not enabled in your browser and may affect website resources. We recommend that you turn it on.
To use the AirGate-3G router to access HTTP service (pages in dynamics HTTP) hosted on the NOVUS FieldLogger equipment.
In this scenario, the FieldLogger is connected by cable to a router with 3G connectivity (the AirGate-3G). It is necessary to configure the port forwarding in the NAT table of the router so that it can properly forward the requests from the FieldLogger.
The router's IP address for the WAN interface is assigned by the telephone network carrier, therefore, because this IP address is dynamic, after every change to the IP address it would be necessary to reconfigure the supervisory software. To avoid this problem the 3G router should use a Dynamic DNS (DDNS) server that translates a dynamic IP into a URL address (HOST). Therefore the FieldLogger needs to maintain the same IP address (static or behind the DHCP server configuration) for the configuration to work correctly.
Figure 1 - Network Topology
Some of these services are subscriptions and others offer limited plans for free. Basically these services attribute a friendly name to the IP address used by the router. To configure the DDNS server [see tutorial TCN001-15]. It is still necessary to define/configure the following parameters:
1.2 Verify the status of the AirGate-3G:
Verify the status of the connection through the system tab, in the web GUI configuration for the AirGate-3G. If the RUN LED is GREEN/BLINK this indicates that the router is ready, as indicated in Figure 2. For more information on how to access the configuration interface of the AirGate-3G, download the manual:
Figure 2 – Indicator LEDs.
Under the tab Current WAN Link, it is possible to verify the IP address assigned by the telephone carrier, as can be seen in Figure 3.
Figure 3 - Current WAN Link.
As can be seen in Figure 4, under the tab Cellular Information, it is possible to verify the general status of the modem, including the APN, carrier and signal quality.
Figure 4 – Cellular Information
1.3 Configuration of the AirGate-3G:
In this tutorial, we will use the DHCP server of the AirGate-3G to assign an IP address to the FieldLogger. Under the Eth1 tab it is possible to verify the IP configuration for the AirGate-3G router in the IP address field (see Figure 5 ); and under the DHCP Server tab, the range of IP addresses assigned to the DHCP. Note that the IP address assigned to the FieldLogger is displayed in the IP lease section, as shown in Figure 6. The value shown in the MAC address field should correspond with the MAC address of the FieldLogger.
Figure 5 – LAN Interface Eth1
Figure 6 – DHCP Server and address leases.
It is necessary to configure the NAT table in the port forwarding to send connection requests to the desired service ports. In Figure 7, all of the connections are being routed to the service port 502 [for communication/configuration] and port 80 [HTTP services].
Figure 7 – NAT Configuration.
1. Configuration of the FieldLogger:
After verifying the configurations of the AirGate-3G and checking the electrical connections, we need to configure the network interfaces of the FieldLogger as shown in Figure 8. For more information please download and consult the operations manual:
Figure 8 – IP Configuration.
In the configuration of the FieldLogger equipment, in the Ethernet Interface it necessary to enable HTTP services [To enable the presentation of dynamic HTML pages] and Modbus TCP [for communication and configuration of the equipment and to allow access to SCADA software]. This can be seen in Figure 9.
Figure 9 – Configuration of HTTP and Modbus TCP
Using this tutorial, it is possible to remotely Configure FieldLogger equipment, Monitor variables through HTTP service, Collect data from the device memory and Display the information through SCADA software. Figure 10 demonstrates different ways to connect to the internet: Wired connection, connection via a WIFI router or access through the cellular network using a mobile device with a 3G data plan.
Figure 10 – Connections and Access to the Internet.
Fieldlogger was the chosen solution to measure temperature and vibration of lift pumps at the wastewater treatment plants of the company located in São Paulo. With proper monitoring, it is possible to prevent problems and save on engine maintenance.
TxIsoRail-HRT and TxIsoBlock-HRT bring the robustness of NOVUS devices combined with HART® protocol certification, recognized worldwide as an industry communication standard for smart field devices.
The pressure measurement procedure is widely widespread within industrial processes and the reliability of these measurements is related with trade, quality, health and safety issues. In this way, a wrong measurement can create problems in the quality of the industrial process and even fatal accidents. In this article, you will find some definitions and the importance of metrology within the industry.
The NP785 can operate bi-directionally, providing the ability to measure differential pressure ranges from vacuum to positive pressure. Designed for HVAC systems and industrial environment, it ensures temperature compensation for long-term stability and complies with electromagnetic compatibility standards.
DigiRail Connect can be used as a slave device in Modbus RTU networks that have RS485 interface or as a server device in Modbus TCP networks that have Ethernet.
NOVUS is committed to protect the privacy and security of your personal information. The data that you share with NOVUS allows us to provide a better experience when you use our products and services. We guarantee total privacy to your data, used exclusively for communications between NOVUS and you.
In this statement we affirm: